1 KOMPKT REGO Reu OTK EN CZ PL Installation and Operation Manual 3 Instalační manuál 32 Instrukja montażu 60
3 EN Content 1. TRNSPORTTION RIEF ESCRIPTION OF THE UNIT INSTLLTION Maintenane spae requirements Setion-to-setion joints Heating oil onnetion MINTENNCE TECHNICL INFORMTION ELECTRICL INSTLLTION MNUL ir Handling Units Setions Connetion Eletri Power Supply Connetion External Elements Connetion Temperature Sensors Installation Control Panel Installation OPERTION MNUL Unit Control Swithing on the Unit Control Panel Indiation Parameters Review Quik Ventilation Level Swithover Unit Programmable Settings Other Control Funtions Unit PC ontrol Troubleshooting SFETY REQUIREMENTS This symbol indiates that this produt is not to be disposed of with your household waste, aording to the WEEE iretive (2002/96/EC) and your national law. This produt should be handed over to a designated olletion point, or to an authorised olletion site for reyling waste eletrial and eletroni equipment (EEE). Improper handling of this type of waste ould have a possible negative impat on the environment and human health due to potentially hazardous substanes that are generally assoiated with EEE. t the same time, your ooperation in the orret disposal of this produt will ontribute to the effetive usage of natural resoures. For more information about where you an drop off your waste equipment for reyling, please ontat your loal ity offie, waste authority, approved WEEE sheme or your household waste disposal servie. U MLV we reserve the right to make hanges without prior notie. 3
4 EN 1. Transportation The air handling units are ready for transit and storage (1 Piture). The unit is paked to prevent damage of the external and internal parts of the unit, dust and moisture penetration. Corners of the air handling units are proteted against the damage protetive orners are used. The entire unit is wrapped up in protetive film. For transit or storage, units are mounted on timber pallets. The unit is fastened to the pallet with polypropylene paking tape over protetive orners Vertial and horizontal units ready for transit and storage 1 Piture When unit is loaded or unloaded by rane, argo rope is fastened in its designated plaes. Forklift truk or hand pallet truk an transport air handling unit as it is shown (1 a, b, Pitures). Vertial and horizontal unit transportation by forklift truk, hand pallet truk or rane 1 a Piture 1 Piture 1 a Unit is transported by forklift truk on a wooden pallet; 1 b Unit is transported by hand pallet truk on a wooden pallet; 1 Unit is lifted by rane on a wooden pallet. 1 b Piture The unit should be examined upon reeipt, to ensure that no visible damage has ourred during transit, and the advie note heked to ensure that all items have been reeived. If damage or delivery shortages are diso vered, the arrier should be immediately informed. MLV should be notified within three days of reeipt, with a written onfirmation sent within seven days. MLV an aept no responsibility for damage by unloading from arrier or for subsequent damage on site. If the unit is not to be installed immediately, it should be stored in a lean, dry area. If stored externally, it should be adequately proteted from the weather. U MLV we reserve the right to make hanges without prior notie.
5 2. rief esription of the Unit Casings of air handling units are made of galvanized steel sheets, whih are powder painted. Mineral wool is used for thermal insulation and sound attenuation. Unit over panels are 5 mm thik. The air handling units are intended for ventilation of medium-sized spaes (eg. single family houses, offies, et.), having operating ambient temperature and relative humidity. s standard, the unit is designed for indoor plaement. The operating temperature range for the unit is C C, outdoor air temperature. The air handling unit is not to be used to transport solid partiles, even not in areas where there is a risk of explosive gases. REGO is equipped with a rotary heat exhanger, RECU - with plate heat exhanger, whih may be replaed with summer assette, when reuperation is needless, air filters, an eletri or water heater, fans and automation ontrol system, to ensure safe and effiient operation of the unit. efore you open the door, the unit must be swithed off and the fans must have been given time to stop (up to 3 minutes). The unit ontains heating elements that must not be touhed when they are hot. To maintain a good indoor limate, omply with regulations and, to avoid ondensation damage, the unit must never be stopped apart from during servie/maintenane or in onnetion with an aident. If the unit is plaed in spaes with high humidity, ondensation might our on the surfae of the unit when outdoor temperatures are very low. Under onditions, when the outdoor air temperature is low and humidity is high, risk of heat exhanger frosting may appear. For this reason anti-frost protetion funtion is foreseen in the ontroller of the Komfovent air handling units. epending on the type of the reovery, different methods of anti-frost protetion are available: old air by-passing, or / and supply air fan speed reduing. For extremely low outdoor air temperature the dut mounted preheater is reommended. Counter ross flow heat exhanger is the mostly sensitive for low outside air temperatures, as the risk of frosting appears in the temperature range from 0 to -5 0 C and below. Standard aluminium ross-flow plate heat exhanger has better features, as the risk of freezing appears only at C. The lowest risk and the highest resistane to old outside air is a ompetitive feature of the rotary heat exhanger, as it is not freezing even at the temperatures of C if the humidity level of the air is appropriate. ir Handling Units Shemes REGO 00/500/700HE(HW)** - R* REGO 900/1200HE(HW) - R* REGO1600/2000/2500HE/HW - R* REGO 3000/000/500/7000HE/HW - R* U MLV we reserve the right to make hanges without prior notie. 5
6 EN REGO 00/500/700VE(VW)** - L* REGO 900/1200VE(VW)** - L* REGO 1600/2000/2500VE - L* REGO 3000/000/500VE - L* REGO 1200PE(W*)* RECU PE(W*)* RECU 700VECF 9 RECU 00/700/900VE(VW)** - L* 9 RECU 1200/1600VE(VW) - L* RECU 00/700/900HE(HW)** - R* RECU 700HECF - R* 6 U MLV we reserve the right to make hanges without prior notie.
7 RECU 1200HE - R* RECU 1200HW - R* RECU 1600/2000HE - R* RECU 1600/2000HW - R* RECU 3000/000/500/7000HE/HW - R* OTK 1. Rotary heat exhanger 2. Plate heat exhanger 3. Eletri or water air heater. Supply air filter 5. Exhaust air filter 6. Supply fan 7. Exhaust fan 8. ir by-pass damper 9. Condensate drain (the water trap must be installed =28 mm) 10. rop eliminator 11. Connetion of main able 12. Fluid onnetion tube Outdoor intake Supply air Extrat indoor Exhaust air * R - right inspetion side. * L - left inspetion side is mirror view of the right. ** uted water heater. 3. Installation 3. 1 Maintenane spae requirements It is reommended to install the air handling unit in a separate room or in the atti on a hard smooth surfae insulated with a rubber mat. The plae for the unit should be seleted with allowane for minimum aess to the unit for maintenane and servie inspetion. The minimum free spae in front of the ontrol panel should be not less than 700 mm. The free spae over the top of the unit should be at least 300 mm (3.1.1 a, b Piture). Rubber mat must be used when unit is going to be mounted on the wall. U MLV we reserve the right to make hanges without prior notie. 7
8 EN Minimum Maintenane Spae for Horizontal Units Minimum Maintenane Spae for Vertial Units. 100 mm 100 mm a Piture min. 700 mm min. 700 mm b Piture REGO RECU unit Installation Sheme view 2 2 view ir handling unit 2. ir dut onnetions 3. Sound attenuator. rain siphon (only RECU) 5. Rubber mat (not inluded in unit set) OTK Maintenane spae for unit min. 700 mm Floor a Piture b Piture min. 100 mm min mm eiling 8 U MLV we reserve the right to make hanges without prior notie Piture* * - only PE.
9 REGO 1200P/REGO P d Piture eiling 1. ir handling unit 2. uts onnetion 3. Sound attenuator. Rubber mat (not inluded in unit set) 5. Holder(see Piture) 6. Ceiling holder (inluded in unit set) 6 Unit holder is made of 2,5 mm galvanized steel sheets aording to EN Condensate rain Connetions ll ondensate drain onnetions must be orretly trapped. Inorret trapping an result in flooding within the unit and onsequent flooding of the immediate area. Fill the drain trap with water before starting up the unit. ll drain lines should be insulated where passing through any spae where damage from ondensation drip might our. If the unit is installed in unheated premises the ondensate pipe should be heat-insulated and heated with heating able. ondensate pipe and a drain trap rain sheme of Vertial Unit rain sheme of Horizontal Unit view 1 view 2 view 2 min. 60 mm min. 30 mm * a Piture b Piture * RECU , REGO =15 mm RECU , REGO =28 mm 3.2 Setion-to-setion joints ir handling units REGO 3000, REGO 000, REGO 500, REGO Setion Connetion Sheme 7000, RECU 7000 are produed from three setions, and RECU 3000, RECU 000, RECU 500 from two setion. Separate setions are easy to install on site. Ensure that setions or setion assemblies are positioned in their proper sequene and that the unit handing and referene is orret. Setions should be aurately aligned prior to bolting together using the fixings and gaskets provided. The sealing gasket and fastening parts are available with every air handling unit. Inorret installation will result in air leakage, air blow marks to the unit asings and unaeptable noise. Setion onnetion sheme is shown in 3.2 Piture. 3.2 Piture 3.3 Heating oil onnetion* Pipe work should be onneted in aordane with good engineering pratie. ll pipe work must be adequatelysupported to ensure that no additional load is stressing the unit. Mounting the pipes on the heating oil, tight the pipes with spanners. s shown in 3.3 Piture. Fitting Pipes Connetion min. 30 mm * min. 60 mm 3.3 Piture U MLV we reserve the right to make hanges without prior notie. 9
10 EN The pipe work should be done in order to ensure the spae for maintenane and servie work. When arrying out the installation of heater pipes, make sure that hot water supply is ompletely disonneted. efore start-up of the air handling unit, the heater system should be filled in with water. Glyol is used in the air handling units with oil heat exhanger. Never pour glyol down a drain; ollet it in a reeptale and leave it at a reyling entre or the like. Glyol is highly dangerous to onsume and an ause fatal poisoning or damage the kidneys. Contat a dotor! void breathing glyol vapour in onfined spaes. If you get glyol in your eyes, fush them thoroughly with water (for about 5 minutes). *If water heater build in. When operating air handling unit in the temperatures lower than 0 C, it is neessary to use glyol additionally or assure the reversible heating agent temperature more than 25 C. It is important to maintain air heaters and oolers leanliness; that is to hange filters installed in the air handling unit on time. If the air heater or ooler gets dirty, to perform periodial leaning. utwork The air flows in/out air handling unit through dutwork. We reommend using galvanized steel (Zn 275 gr/m 2 ) dutwork, to ensure easy leaning and durability. It is neessary to use the dutwork system with low air flow rate and small pressure drop to have neessary air volume and low sound level and save the energy. The appropriate sound attenuators will redue the noise level of the fans in the premises. ll dutwork should be insulated with mm thikness insulation to avoid the ondensation. Note: temperature sensor 1 has to be mounted in the supply air dut under eletri heater (see the funtional diagram in Control System Eletrial Installation and Operation Manual). It is neessary to leave spae in straight air dut for sensor mounting and guarantee the spae for maintenane and servie work. Minimal spae between the unit and 1 sensor is the spae of double air dut diameter. utwork, steelwork and any other servies should not be supported off the unit. In dut system, for units with eletri air heater, use air losing damper without spring return mehanism. Final Inspetion fter installation of the unit, a thorough inspetion should be arried out. This should inlude inspeting the inside of the unit and removing debris and tools, whih may have been left behind by on site ontrators. Replae any panels, whih may have been removed and lose all aess doors, ensuring that the door sealing gaskets have not been damaged.. Maintenane It is reommended to arry out routine maintenane of the air handling unit REGO/RECU/OTK, 3 times per year. REGO 1200P use the key to open the door. o not release the door to swing freely, but open it slowly at a 90 degree angle. e areful while opening, beause logged filters might fall out. esides preventive maintenane inspetion, the following operations should be performed: 1. Rotary heat exhanger hek. Inspetion of the rotary heat exhanger is performed one per year. Free rotation of the rotary heat exhanger, ontinuity of the rotating belt, absene of damages of the rotor drums and the seal gasket are heked. It is neessary to hek the streth of belt. Free belt will slide and the effiieny of rotary heat exhanger will fall down. To reah maximal effiieny, rotor must turn at least 8 times per minute. Polluted heat exhanger will derease effiieny. Clean heat exhanger with an air blast or wash with tepid water. Chek out water falling on the eletri motor. 2. Plate heat exhanger hek. Inspetion and dedusting of the plate heat exhanger is performed one per year (it is removed from the unit and blown with an air blast or washed with tepid water). Note: plate heat exhanger may be replaed with summer assette, when reuperation is needless. 3. Fans hek (one per year). Polluted fans derease effiieny. efore performing any inspetion work, hek whether the unit is swithed off from the eletri power supply. 10 U MLV we reserve the right to make hanges without prior notie.
11 Fans should be arefully leaned with textile or soft brush. o not use water. o not break balane. Chek if diretion of fan turns is right, beause wrong diretion of turns gives only 30% rating. Chek if fan freely rotates and is not mehanially damaged, if impeller does not touh sution nozzles, fan does not spread noise, the pressure tubes are onneted to the nozzle (if it is required), mounting bolts are srewed. The rubber ouplings onneting the motor base and the unit should be visually inspeted for signs of wear and replaed as neessary. ny unusual noise or vibration when the fan is running should be immediately investigated, as this usually an indiation of wear or imbalane in the fan system.. ir heater hek. Reommended to perform periodial inspetion and leaning of heater. Chek the plates of water air heater. The air heater is leaned with hoover from supply air side or with air blast from exhaust air side. If it is very dirty, wash with tepid water, whih will not make orrosion of aluminium. Chek if position of return water temperature sensor is right. Chek if eletri air heater is properly fixed, wires onnetions are not damaged and heating elements are not bent. They an be damaged or bent due to uneven heat or uneven and turbulent air diretion. Chek if eletri air heater is lear of unneessary things and heating elements are not logged, beause this an ause unpleasant smell or in the worst ase dust an start burning. Heating elements an be leaned with hoover or wet textile. 5. ir damper hek (if it is required). Not fully opened outside air damper rises up the pressure in the system. Water air heater an freeze if outside air damper does not fully lose in not working air handling unit. Mounting and running of air damper should be heked and regulated. 6. ir filter logging hek. Change air filters when air filter logging is indiated. We reommend to hange filters at least twie per year: before and after heating season, or more*. Filters are one time used. We do not reommend leaning them. Stop the air handling unit before hanging filters. Pressure sensor Piture 7. Pressure sensor setting, whih indiates impurity of filters. Pressure sensor is set aording to EN 13779:2007 standard: 100 Pa for small systems, 150 Pa for big systems. Remove over from the pressure sensor and turn the ursor due to proper position. The indiator will turn on when filters will be logged. One of pressure sensors shown in Piture an be mounted in the air handling unit. Close the door after pressure sensor regulating proess. e sure that sensor does not indiate impurity of lear filters. Pressure sensors in the air handling units up to size 900 are regulated and set in fatory. * Clogged filters unbalane ventilation system, air handling unit uses more power. U MLV we reserve the right to make hanges without prior notie. 11
12 EN 5. Tehnial Information REGO RECU Horizontal units REGO RECU Vertial units OTK Type REGO Parameters Width, W imensions Length, L/l (L 1, L 2, L 3 ) 1 Height, H/h Weight Supply voltage Operating urrent Heater apaity Hot water Eletri Fans input power uts onnetion mm mm mm kg V kw 2 kw W mm 00HE-EC / ~ 230 6,2 1 2* HW-EC / ~ 230 2,3 2,65 2* HE-C / ~ 230 5,8 1 2* HW-C / ~ 230 2,0 3,0 2* HE-EC / ~ 230 6,9 1 2* HW-EC / ~ 230 3,0 3,0 2* VE-C / ~ 230 5,8 1 2* VW-C / ~ 230 2,0 3,0 2* VE-EC / ~ 230 6,9 1 2* VW-EC / ~ 230 3,0 3,0 2* HE-C / ~ ,8 2 2* HW-C / ~ 230 2,8,5 2* HE-EC / ~ ,5 2 2* HW-EC / ~ 230 3,2,5 2* VE-C / ~ ,8 2 2* VW-C / ~ 230 2,8 3,6 2* VE-EC / ~ ,5 2 2* U MLV we reserve the right to make hanges without prior notie.
15 Type OTK Parameters Width, W imensions Length, L/l (L 1, L 2, L 3 ) 1 Height, H/h Weight Supply voltage Operating urrent Heater apaity Hot water Eletri Fans input power uts onnetion mm mm mm kg V kw 2 kw W mm 700PE/ / ,5 1x230 13, PE/ / ,5 3x00 9, PE/ / ,5 3x00 13, PE/ / ,5 3x00 1, PE/ / ,5 3x00 23, PE/ / ,5 3x00 2,2 15 2x x PE/22, / ,5 3x00 35,1 22,5 2x x PW / ,5 1x230 1, PW / ,5 1x x x PW / x00 2, x00 000PW / x00 2, x00 Parameters with nominal air volume, t outside = C, t inside = 22 0 C. 1 (L 1,L 2 ) setional unit. 2 Parameters of hot water C, onnetion REGO 1/2, REGO 000HW/VW and RECU 1 3 3~ 230V is available as an option. ir heater and ooler ombined in one water oil. RECU , REGO uted H water heater. imensions of utwork Connetion Type Parameter w 1 w 2 w 3 w l 1 l 2 l 3 l h 1 h 2 h 3 h mm mm mm mm mm mm mm mm mm mm mm mm REGO 00HE(W) /700HE(W) /700VE(W) HE(W) VE(W) HE(W) VE(W) P /2000/2500HE(W) /2000/2500VE(W) /000/500VE(W) /000/500HE(W) HE(W) RECU 00HE(W) VE(W) HE(W) VE(W) HE(W)CF VE(W)CF HE(W) VE(W) HE(W) U MLV we reserve the right to make hanges without prior notie. 15
16 EN Parametrai w 1 w 2 w 3 w l 1 l 2 l 3 l h 1 h 2 h 3 h Tipas mm mm mm mm mm mm mm mm mm mm mm mm 1200VE(W) /2000HE(W) /2000 P VE(W) /000/500HE(W) HE(W) OTK Filters Unit Type Overall dimensions Supply Exhaust Type Width Height Length Length REGO 00 PF5/PF7* REGO 500/700 PF5/PF7* REGO 900/1200V F5/F7* REGO 900/1200H PF5/PF7* REGO 1200P PF5/PF7* REGO 1600/2000/2500V PF5/PF7* REGO 1600/2000/2500H PF5/PF7* REGO 3000/000/500 F5/F7* REGO 7000 F5x2/F7*x RECU 00 PF5/PF7* RECU 700/900 PF5/PF7* RECU 700CF PF5/PF7* RECU 1200/1600 F5/F7* RECU 1600H/2000 PF5/PF7* RECU 1600/2000 PF5/PF7* RECU 3000/000/500 F5/F7* RECU 7000 F5x2/F7*x OTK 700PE PF OTK 1200PE PF OTK 2000PE PF OTK 1200PW PF OTK 2000PW PF OTK 3000,000PW PF5x2/PF7*x Supply/Exhaust air REGO RECU PF5 Panel, lass M5 (EN779) PF7 Panel, lass F7 (EN779) F5 ag filter, lass M5 (EN779) F7 ag filter, lass F7 (EN779) * - F7 lass filter is available as an option 16 U MLV we reserve the right to make hanges without prior notie.
17 6. Eletrial INSTLLTION MNUL Installation works an be performed only by the speialists that have required qualifiation. uring installation following requirements must be fulfilled. It is reommended to lay ontrol ables separately from power ables, or use shielded ables. In suh ase it is neessary to earth able shielding! 6.1. ir Handling Units Setions Connetion fter unit parts have been onneted together (see unit installation instrution), unit setions onneting ables and wires are onneted. Connetor onnetion is performed stritly aording to numeration given in wiring diagram, or adequate markings (see unit eletri sheme). When disonneting unit setions, do not pull by onneting wires and ables! 6.2. Eletri Power Supply Connetion If the air handling unit voltage is ~230V; 50 Hz it is neessary to install the soket with grounding of orresponding apaity (see eletri diagram unit). If the voltage is ~00V; 50 Hz, the able of eletrial power supply is onneted to the main swith, whih is loated on the unit s outside wall. It is neessary to onnet earthing! Types of ables of onnetion of eletrial power supply are speified in 6.2 Table: U MLV we reserve the right to make hanges without prior notie. 17
18 EN 6.2 Table Eletrial Power Supply Cable Types ir Handling Unit Type REGO-00HE-EC; REGO-00HW-EC; REGO-500H(V)E(W)-C; REGO-700H(V)E(W)-C; REGO-500H(V)E(W)-EC; REGO-700H(V)E(W)-EC; REGO-900H(V)W-C; REGO-900H(V)W-EC; REGO-1200H(V)W-EC; REGO-1200PW-EC; REGO-1600H(V)W-EC; REGO-2000H(V)W-EC; REGO-2500H(V)W-EC; RECU-00H(V)E(W)-C; RECU-00H(V)E(W)-EC; RECU-700H(V)E(W)-EC; RECU-700H(V)E(W)-C; RECU-700H(V)E(W)CF-EC; RECU-900H(V)W-C; RECU-900H(V)W-EC; RECU-1200H(V)W-EC; RECU-1600H(V)W-EC; RECU-2000HW-EC; OTK 1200PW; OTK 2000PW OTK 700PE3 REGO-900H(V)E-C; REGO-900HE-EC; REGO-1200H(V)E-EC; REGO-1200PE-EC; REGO-1600H(V)E-EC; REGO-3000H(V)W-EC; REGO-000H(V)W-EC; REGO-500H(V)W-EC; REGO-7000HW-EC; RECU-900H(V)E-C; RECU-900H(V)E-EC; RECU-3000HW-EC; RECU-000HW-EC; RECU-500HW-EC; RECU-7000HW-EC OTK 700PE6; OTK 3000PW; OTK-000PW-EC REGO-2000H(V)E-EC; REGO-2500H(V)E-EC; REGO-3000H(V)E-EC RECU-1200H(V)E-EC OTK 700PE9; OTK 1200PE9 RECU-1600H(V)E-EC OTK 1200PE15; OTK 2000PE15 RECU-3000HE-EC; REGO-000H(V)E-EC; REGO-500H(V)E-EC RECU-2000HE-EC; RECU-000HE-EC; RECU-500HE-EC OTK 2000PE22.5 Cable type 3 x 1,5 mm 2 (Cu) 3 x 2,5 mm 2 (Cu) 5 x 1,5 mm 2 (Cu) 5 x 2,5 mm 2 (Cu) 5 x,0 mm 2 (Cu) 5 x 6,0 mm 2 (Cu) 5 x 10,0 mm 2 (Cu) ir handling units designed for 00V C supply voltage must be onneted to the stationary installation by solid able. ll units must be onneted through iruit breaker with max. 30m urrent leakage protetion. efore onneting unit to the eletrial power supply, it is neessary to hek whether earthing has been installed properly External Elements Connetion In the air handling unit it is provided onnetion board 6.3 a piture or 6.3 b piture (depending on the unit type), all external elements are onneted to onnetion board. External elements onnetion diagram is given in the 6.3 piture or 6.3 d piture. Connetion oard P3 Connetion oard C3-P1 6.3 b Piture 6.3 a Piture 18 U MLV we reserve the right to make hanges without prior notie.
19 6.3 Piture P3 Control System External Elements Connetion iagram Control ontat. o not onnet voltage! ir handling units designed for 00V C supply voltage must be onneted to the stationary installation by solid able. ll units with air flow up to 2000 m3/h (inlusively) must be onneted through iruit breaker with max. 30m urrent leakage protetion, and units from 3000 m 3 /h - with 300m urrent leakage protetion. Normally losed ontat. o not onnet voltage! 1 used only in the units with water heater. 2 additional ordered funtion, only with EC fans. 3 In OTK unit is not used. In units with C fans is not used. U MLV we reserve the right to make hanges without prior notie. 19
20 EN 6.3 d Piture C3-P1 Control System External Elements Connetion iagram Normally losed ontat. o not onnet voltage! Control ontat. o not onnet voltage! 1 used only in the units with water heater. 2 additional ordered funtion, only with EC fans. 20 U MLV we reserve the right to make hanges without prior notie.
21 6.. Temperature Sensors Installation Supply air temperature sensor 1 (6. a Piture) is mounted in the air dut in a projeted plae for it; after eletri heater or ooler setion (if provided). The minimal distane from the air vent of the unit up to the sensor should be not less than double diameter of the irular onnetion or a diagonal of retangular onnetion. Water temperature sensor 5 (6. b Piture) is mounted on the return water pipe by srewing it into the provided hole. It is reommended that the sensor would be thermo insulated! Supply air temperature sensor 1 Return water temperature sensor 5 6. a Piture 6. b Piture 6.5. Control Panel Installation 1. Control panel must be installed in the room under given following onditions: 1.1. ambient temperature range 0 0 C C; 1.2. relative humidity limits 20% 80%; 1.3. protetion must be ensured from aidentally vertially falling water drops (IP X2). 2. Installation height must be not less than 0,6 m from the ground. 3. Control panel onnetion is projeted through the hole in its bakside.. Control panel is fixed after srewing two holes on the fastening surfae. Control panel is onneted to the onnetion box terminals (see 6.3 a Piture) to the provided terminals (6.3 b Piture). The length of the able between the ontrol panel and the unit should not exeed 150 m. Cable type is speified in unit wiring diagram. Control Panel Connetion 6.5 Piture When losing the panel window, do not bend the springs inside as this may inhibit the funtions of the panel buttons! isonnet power supply prior to onneting the ontrol panel! Control panel onnetion and other able thiknesses are speified in the wiring diagram! U MLV we reserve the right to make hanges without prior notie. 21
22 EN 7. Operation manual 7.1. Unit Control ir handling units ontrol system ensures ontrol of the physial proesses that are taking plae inside the air handling unit. Control system onsists of: ontroller board; fuses, power and intermediate ontrol boards, whih are installed inside the unit; ontrol panel, whih an be installed in the onvenient plae for the user; air damper atuators; pressure and temperature sensors. Control panel (7.1 Piture) is designed for remote air handling unit ontrol, setting and display of ontroller parameters. Control panel LC display with baklight allows monitoring various parameters and text messages. Controller light signals indiate unit operation modes and failures. ir temperature, ventilation intensity, operation modes and other parameters are set by the touh sensitive buttons. General View of the Control Panel Touh sensitive buttons loated on the panel mean: 7.1 Piture start up and shut down of the air handling unit / return to previous menu window; entry to parameters hange menu / set parameters onfirmation; navigation in the menu / parameters value hange Swithing on the Unit fter onneting the unit to the eletrial power supply, on the ontrol panel LC displays start-up window, this is shown in the Piture 7.3. Unit is swithed on (off) by touhing and holding button for seonds till sound onfirms the ation. fter swithing on, unit will start operating after short delay (about 60 seonds), until air dampers open up, and fans start running. Unit operation is indiated in the ontrol panel by ventilation intensity and LE signals (see further). o not swith on the unit without onneted earthing! Make sure, whether all unit setions are tightly interonneted Control Panel Indiation ata is presented to the user on the ontrol panel LC display by numbers and text messages, also by two olour LE signals. Controller display start-up window is shown in the 7.3 Piture. 22 U MLV we reserve the right to make hanges without prior notie.
23 Temperature mode symbols (, ) utomati mode symbol Control Panel Start-Up Window Setting temperature ( C) Time 7.3 Piture Ventilation level (0,1, 2, 3) Supply air temperature Unit operation indiation LE Current season (Winter / Summer) Light iode Indiation: 1. No LE signal indiation on the panel unit has been swithed off. 2. LE shines steady green and text message is shown unit is swithed on. 3. utomati mode symbol is shown on the panel, while green LE shines unit is operating in automati mode aording to weekly shedule.. LE blinks red and green and text message is shown see 7.9 hapter. 5. LE shines steady red and text message is shown emergeny unit shut down (see 7.9 hapter). 6. Nothing is showing on the ontrol panel - unit does not have eletri power supply. 7.. Parameters Review Main parameters are shown in the start-up window (7.3. Piture). To view other parameters (temperature value or air flow indiation) touh, buttons till orresponding window appears: *Exhaust air temperature and flow are not displayed for OTK units The 3rd window is provided only in the units with EC fans. There is possibility to hange air flow indiation from m 3 /h to m 3 /s or l/s. ll you need to do is to press button while being in an air flow indiation window and holding this button go up and down with, buttons till you selet the right measures. The th window is provided only in the units with EC fans. epending on the type of mounted air quality sensor, the th window may appear in one of three ways. It appears when air quality funtion is ativated (see ir quality funtion setting). U MLV we reserve the right to make hanges without prior notie. 23
24 EN 7.5. Quik Ventilation Level Swithover Three ventilation levels are projeted in the unit. Eah of them has its intensity (more detailed settings see in the next hapter). There is possibility to swith ventilation level quikly from start-up window (7.3 Piture). To inrease ventilation intensity: touh and hold and at the same moment inrease ventilation intensity by touhing button. To derease ventilation intensity: touh and hold by touhing button. and at same moment derease ventilation intensity If ventilation intensity is hanged using quik swithover and unit is operating aording to weekly shedule, operation mode automatially is hanged to manual mode Unit Programmable Settings y soft touhing button the parameters menu is entered. Menu window is seleted by buttons, (see further desription). When menu window is seleted, touh value with,. To onfirm the hanges touh. for seleting desirable parameters and selet the To return to previous menu or to start-up window touh button. Note: If touh sensitive buttons are inative for 1 minute, start-up window is shown. 1. Unit operation modes setting Two unit operation modes are possible: manual and automati. In manual mode unit operates ontinuously by set ventilation intensity. In automati mode unit works aording to weekly shedule (see further weekly shedule setting). Note: If automati operating mode is seleted, there is a symbol in the start-up window. 2. ir volume ontrol setting Supply and exhaust air volumes ontrol modes have been projeted in the unit: Constant air volume (CV) ontrol mode - unit supplies and exhausts onstant air volume preset by the user, independent of the proessing hanges in the ventilation system; Variable air volume (VV) ontrol mode - unit supplies and exhausts air volume orrespondingly to the ventilation requirements in different premises. In ase of frequently hanging ventilation demands this air volumes maintenane mode signally redues unit exploitation osts. Menu window for air volume ontrol setting is provided only in the units having air flow maintenane funtion. Only with EC fans. If air handling unit is provided with variable air volume ontrol funtion, primary ontrol mode alibration (look further) is essential, otherwise after hoosing VV mode unit will not operate. Variable air volume ontrol mode alibration: 1. efore ativating the devie you should adjust air distribution and exhaust devies in ventilation system, open all valves for variable air flow in a way enabling air supply to all ventilated premises. 2. Swith on the unit and by hoosing menu window for air volume ontrol setting (see above) atuate onstant air volume maintenane mode. 3. fter hoosing the CV mode and being at the same menu window touh both and buttons at the same moment. fter this, alibration will start for 3 minutes and during this time unit will start working on maximum ventilation intensity and there will be displayed Wait... on the ontrol panel. uring alibration proess all buttons are inative, exept whih allows to shut down the unit and stop the alibration.. fter finishing the alibration proess, air handling unit further will operate in the previously settled mode. 2 U MLV we reserve the right to make hanges without prior notie.
25 3. Setting ventilation level Three ventilation levels have been projeted in the unit: 1, 2 and 3. Eah of these levels may be set for manual or automati operation mode. To set ventilation level in manual mode, selet menu window: Note: In the air handling units provided with the air flow maintenane funtion for eah of three ventilation intensity levels maintained air flow an be adjusted and set separately for supply and exhaust air. It an be set from 20 up to 120% by 1% steps. ir handling unit is designed and alulated to operate on maximum 100% intensity with exeptions when intensity might be set more than 100%.. Exhaust air flow orretion Set air flow intensity (or maintained air volume) for 1-99 minutes period an be orreted from -50% till +50% from set value. Example: after reduing exhaust air flow intensity, for some time overpressure will be aused (sometimes needed to start the fireplae or suh). On - orretion funtion on. Off - funtion off. Note: fter this funtion has been ativated unit will work for the set time period with present exhaust orretion. fter time period is over this funtion turns off automatially. This funtion is not provided in the units with C fans. 5. Setting temperature maintenane mode Several temperature maintenane options are provided in the air handling unit: supply air maintenane, room (exhaust) air maintenane, automati. fter seleting uto, when ooling is needed, unit will work in the room temperature maintenane mode. If the outside temperature will be few degrees lower than set value, ontrol automatially will swith to supply air maintenane mode. 6. Setting temperature value ir handling unit maintains preset temperature by the user: supply air or room, depending on whih ontrol has been seleted (see temperature ontrol mode setting). Note: If before that supply air temperature maintenane mode was set, in the start-up and temperature value setting window symbol is indiated; if room temperature maintenane Setpoint sliding The setpoint an be shifted from -9 to +9 0 C from the temperature set value at speified by user time period. To set setpoint sliding selet menu window: 8. ir quality funtion setting To set the air quality (Q) funtion selet menu window: U MLV we reserve the right to make hanges without prior notie. 25
26 EN On - Q funtion on. Off - funtion off. fter funtion is ativated, the type of sensor, whih is onneted to the unit, is seleted: VOC1 (Volatile Organi Compound) air quality sensor having signal-dependent linear relationship, the maximum value of output signal orresponds to the highest air quality. VOC2 air quality sensor having inverse relationship, the maximum value of output signal orresponds to lowest air quality. RH relative humidity sensor. CO 2 arbon dioxide sensor. epending on the sensor type, the value of Q funtion is set, aording to it the intensity of the unit is regulated. If atual air quality value varies from the setpoint then ventilation intensity will inrease otherwise derease. For instane, if the humidity maintaining system is designed in the devie, and there is additional relative humidity (RH) sensor, then by setting 65% in the air quality window, and by regulating the intensity of ventilation automatially, humidity of 65% will be maintained, i.e. if humidity inreases, ventilation intensity will be inreased as well, and if humidity redues, the devie will swith bak to the previous mode. This funtion is not provided in the units with C fans. 9. Season setting For the air handling unit operating in most eonomial mode, summer and winter seasons have been provided. y setting Winter season, unit ooling funtion is bloked. y setting Summer season, unit heating funtion is bloked. y setting uto, automati season seletion will take plae. epending on the heating and ooling demand, the season is seleted automatially. To set season selet menu window: Note: If air temperature during summer season is insuffiient, air handling unit an be preset and for Winter season mode, its energy expenditures will be minimal. 10. ay and time setting For the unit proper operation in automati mode aording to preset weekly shedule the day of the week and time should be set: ays notation: Mo Monday Tu Tuesday We Wednesday Th Thursday Fr Friday Sa Saturday Su Sunday 11. Weekly shedule setting Two ways for weekly shedule setting have been projeted: 1-5/6,7 - simplified shedule setting option: one shedule for all work days and the other for weekend operation; weekly shedule setting option: different operation shedule for eah day. There is one operation shedule with two setting options. 26 U MLV we reserve the right to make hanges without prior notie.
27 fter seleting program for eah day of the week 1-7 shedule setting window is introdued: Eah day of the week has 3 events: N1, N2, N3. Settings start from Monday (Mo). When the event of the day is seleted, event start and end time is set and ventilation intensity level (0, 1, 2, 3) is assigned. efore seleting work days and weekend operation mode shedule 1-5/6,7 menu window is introdued: fter event (N1, N2, N3) is seleted for work days 1-5, eah event start and end time and ventilation intensity is set the same way. The same way three unit operating events are set for the weekend: Note: Every event start and end time is set from 0:00 to 23:59 h. For instane: Monday: N1 from 00:00 to 07:00 2 ventilation level N2 from 10:00 to 20:00 1 ventilation level N3 from 20:00 to 23:59 3 ventilation level 12. Language setting Language seletion menu has been projeted on the ontrol panel. To set language the last menu window should be seleted: 13. Menu loking The PIN ode is provided to lok entering to the parameters setting menu. If the menu is loked, only main parameters an be reviewed also the unit may be swithed on or off. To enter the PIN ode, touh + and hold for seonds till orresponding window appears: To enter the PIN ode follow these steps: 1. Touh or to enter the first digit. 2. Touh to go to the seond digit. 3. Repeat the steps above to enter the seond and the third digits.. fter third digit is entered touh to onfirm the ode. 5. Touh and and hold for seonds to save the ode into ontroller memory. The menu an be unloked only with the PIN ode. If the ode is forgotten, ontat loal servie team Other Control Funtions 1. Remote unit ontrol Unit is provided with remote ontrol possibility using external devie (button, timer, other sensor), whih is onneted to the ontats 17, 18 (see hapter 6.3 Piture) or 27, 28 (see hapter 6.3 d Piture). This funtion an perform one of two operations: remote unit swithing on and off; remote unit intensity ontrol (additional ordered funtion). U MLV we reserve the right to make hanges without prior notie. 27
28 EN 1.1. Remote unit swithing on or off If the unit is not operating aording to programmed week shedule, by onneting (short-iruit) ontats 17, 18 (see hapter 6.3 Piture) or 27, 28 (see hapter 6.3 d Piture) unit will be swithed on and will operate with the intensity set in the menu window Ventilation (see page 23); by disonneting ontats unit operation will return to previous mode. If unit is operating in auto mode with hosen intensity, to swith it off by remote swith ontats 17, 18 (see hapter 6.3 Piture) or 27, 28 (see hapter 6.3 d Piture) must be onneted (short-iruit). Remote unit swithing on and off is available only when auto mode is set! 1.2. Remote unit intensity ontrol (OVR)* If this funtion is ordered in advane, unit intensity will be ontrolled by ontats mentioned above. If ontats 17, 18 (see hapter 6.3 Piture) or 27, 28 (see hapter 6.3 d Piture), are interonneted, the fourth level of intensity will be ativated, after disonneting unit will return to previous mode. djusting intensity of the fourth level for supply and exhaust fans is performed in the Ventilation window, only when this funtion is ativated, i.e. when these ontats are short-iruited. Remote unit intensity ontrol has the highest priority and operates in every mode, even the unit is swithed off. Note: This funtion is provided only for the units with EC fans. 2. Ventilation orretion in the winter In wintertime, when heating power is not enough and supply air temperature is below setting value, ventilation intensity automatially is dereasing in one level. If there is not enough, one more level (up to minimum) till set supply air temperature will be maintained. 3. Pump ontrol Units with water heater are designed with water irulation pump ontrol. In winter pump operates ontinually, in summer season it is off. When outdoor temperature is lower than 5 0 C, pump is automatially turned on. Pump is onneted to the onnetion box ontats (see 6.3. hapter).. Cooling energy reovery In summer when room temperature is lower than temperature outside, units with either plate heat exhanger or rotary heat exhanger automatially operate with ativated funtion of ooling energy reovery. This funtion is not provided for OTK units 5. Remote unit operation and failure indiation If the information about unit operation mode is requested (when unit is operating and when is not) indiation devie (for ex. bulb) must be onneted to the ontats 33, 35 (see hapter 6.3 Piture). In the onnetion board (see hapter 6.3.) are provided ontats 33, 3 (see hapter 6.3 Piture) or 29, 30 (see hapter 6.3 d Piture), whih are intended for onnetion of unit s emergeny stop indiating devie. 6. Summer night ooling* If the room temperature (exhaust air) in summertime is 5 0 C higher than the setpoint and outside temperature is between 12 0 C and the setpoint, the ventilation level is automatially swithed to the third intensity level at 00:15 am. The unit will operate in the third intensity level until 06:00 am or when outside air ools down (warms up) too muh or the room temperature equals the setpoint. The air is being ooled only by fans, without heat or oolness reovery and additional air heating or ooling. When funtion is swithed off the unit ontinues operating in the previuos mode. Funtion starts operating automatially if only the unit operates in the first or seond ventilation intensity level. Funtion stops operating, when the ventilation intensity level is being hanged. * - additional ordered funtion Unit PC ontrol This is additionally ordered funtion and for it implementation speial network module Ping2 is provided. Connetion diagrams and installation requirements of network module are given in the Ping2 module installation manual. fter onneting units through speial network modules to omputer network or Internet and given an IP address, integrated web server allows the operator from his omputer not only to monitor, but also to ontrol air handling units operation: to turn on/off, hange ventilation intensity and et. It also allows indiating failures. 28 U MLV we reserve the right to make hanges without prior notie.
Klimatyzatory ścienne i kasetonowe YORK Cennik 2013 ELECTRONIC CONTROL SYSTEMS SP. Z O. O. 32-083 Balice k. Krakowa; ul. Krakowska 84 MODEL / KOMPLET YJHJZH 09 ŚCIENNY YJHJZH 12 ŚCIENNY YJHJZH 18 ŚCIENNY
Zakopane, plan miasta: Skala ok. 1:15 000 = City map (Polish Edition) Click here if your download doesn"t start automatically Zakopane, plan miasta: Skala ok. 1:15 000 = City map (Polish Edition) Zakopane,
UNIWERSYTETU BIBLIOTEKA IEGO UNIWERSYTETU IEGO Instrukcja konfiguracji usługi Wirtualnej Sieci Prywatnej w systemie Mac OSX 1. Make a new connection Open the System Preferences by going to the Apple menu
RAIL TARIFF This Rail Tariff is an integral part of intermodal transport arrangement service provided by PCC Intermodal S.A. and therefore it cannot be used as a standalone offer, only in combination with
Hippo Boombox Instrukcja obsługi User s Manual OPIS PRZYCISKÓW: PL ON-OFF/MODE: 1. Włącz on/off: Naciśnij przycisk, aby włączyć urządzenie. Przytrzymaj dłużej, aby wyłączyć. 2. MODE: Wybierz źródło sygnału:
LED PAR 64 7x10W RGBW 4in1 ABS Remote Control F7100303 USER MANUAL / INSTRUKCJA OBSŁUGI LED PAR 64 7x10W RGBW 4in1 ABS Remote Control F7100303 Table of Contents 1 Introduction... 2 2 Safety information...
POL SKI Instrukcja obsługi miernika zużycia energii Operating Instructions for Power Meter 406-074 PL EN Instrukcja obsługi w oryginale Operating instructions in original 20.06.2011 Jula AB POLSKI ZASADY
Chilli Boombox Instrukcja obsługi User s Manual OPIS PRZYCISKÓW: PL ON-OFF/MODE: 1. Włącz on/off: Naciśnij przycisk, aby włączyć urządzenie. Przytrzymaj dłużej, aby wyłączyć. 2. MODE: Wybierz źródło sygnału:
A n g i e l s k i Phrasal Verbs in Situations Podręcznik z ćwiczeniami FRAGMENT Dorota Guzik Joanna Bruska Autorzy: Dorota Guzik, Joanna Bruska Konsultacja językowa: Tadeusz Z. Wolański Lektorzy: Maybe
K A R T Y K ATA L O G O W E Fixtures LED HEDRION Oprawy lampy LED Hedrion do zastosowań profesjonalnych Fixtures LED lamps Hedrion for professional applications NATRIUM Sp. z o.o. ul. Grodziska 15, 05-870
Typ MFPCR FOR THE MOST DEMANDING REQUIREMENTS ON THE PURITY OF INDOOR AIR, WORKSTATIONS, AND DEVICES HEPA and ULPA filters as high-efficiency particulate filters for the separation of suspended particles
1. Introduction Jazz EB207S is a slim, compact and outstanding looking SATA to USB 2.0 HDD enclosure. The case is made of aluminum and steel mesh as one of the coolest enclosures available. It s also small
2 3 Zasady bezpieczeństwa GB The door and the feeding flap must be closed when operating the machine! PL Drzwiczki i klapka szczeliny podawczej muszą być zamknięte w trakcie używania urządzenia! GB Ensure
WENTYLATORY PROMIENIOWE SINGLE-INLET DRUM BĘBNOWE JEDNOSTRUMIENIOWE CENTRIFUGAL FAN TYP WPB TYPE WPB Wentylatory promieniowe jednostrumieniowe bębnowe (z wirnikiem typu Single-inlet centrifugal fans (with
Indus www.essystemk.com Strona 1/9 Page 1/9 SPIS TREŚCI: 1. Informacje ogólne...3 General information 2. Informacje elektryczne...4 Electrical information 3. Informacje chłodnicze...5 Cooling information
OSTC GLOBAL TRADING CHALLENGE MANUAL Wrzesień 2014 www.ostc.com/game Po zarejestrowaniu się w grze OSTC Global Trading Challenge, zaakceptowaniu oraz uzyskaniu dostępu to produktów, użytkownik gry będzie
1 / 12 Content list / Spis Treści 1. Hardware and software requirements, preparing device to upgrade Wymagania sprzętowe i programowe, przygotowanie urządzenia do aktualizacji 2. Installing drivers needed
LED MOVING HEAD MINI BEAM 18x3W RGB CREE F7000560 USER MANUAL / INSTRUKCJA OBSŁUGI LED MOVING HEAD BEAM 18x3W RGB CREE F7000560 Table of contents 1 Introduction... 2 2 Safety information... 2 3 Maintenance...
Extraclass Football Men Season 2009/10 - Autumn round Invitation Dear All, On the date of 29th July starts the new season of Polish Extraclass. There will be live coverage form all the matches on Canal+
LED PAR 56 7*10W RGBW 4in1 SLIM USER MANUAL Attention: www.flash-butrym.pl Strona 1 1. Please read this specification carefully before installment and operation. 2. Please do not transmit this specification
W6636 East Avenue North, Onalaska, WI USA (608) 781-8500 Fax: (608) 783-6115 F150-80789-D-09 2 3 Model SPECIFICATIONS 4 Informacja o paliwie dla panstwa docelowego Gaz Plynny Panstwa docelowe Kategoria
Typ SCF FITTING OF FILTER ELEMENTS FOR THE SEPARATION OF COARSE AND FINE DUST Standard cell frames for pocket filters, Mini Pleat filter inserts, activated carbon filter inserts, Mini Pleat filter panels
Typ VME FOR THE MEASUREMENT OF VOLUME FLOW RATES IN DUCTS Rectangular volume flow rate measuring units for the recording or monitoring of volume flow rates Manual volume flow rate measuring Permanent volume
ED 0-40 Best compatibility with intelligent s Model: TE40-DIMM-ED-IP64 Application: The Transformer is exclusively designed to supply 12 VDC ED strips and ED s. In the case of use this product there is
Domy inaczej pomyślane A different type of housing CEZARY SANKOWSKI O tym, dlaczego warto budować pasywnie, komu budownictwo pasywne się opłaca, a kto się go boi, z architektem, Cezarym Sankowskim, rozmawia
Tablice zmiennej treści Variable message boards UOPG6 Zadaniem tablic zmiennej treści jest przekazywanie bezpośrednim użytkownikom ruchu informacji o warunkach występujących na drodze oraz treści istotnych
user s manual NV-002MIC NV-002MIC - user's manual, ver. 1.0 INFORMATION EMC (2004/108/EC) and LVD (2006/95/EC ) Directives CE Marking Our products are manufactured to comply with requirements of following
Test sprawdzający znajomość języka angielskiego Imię i Nazwisko Kandydata/Kandydatki Proszę wstawić X w pole zgodnie z prawdą: Brak znajomości języka angielskiego Znam j. angielski (Proszę wypełnić poniższy
Centre Number Surname Candidate Number For Examiner s Use Other Names Candidate Signature Examiner s Initials Section Mark Polish Unit 1 Reading and Writing General Certificate of Education Advanced Subsidiary
LED MOVING HEAD STRONG 108x3W RGBW WASH III F7000579c USER MANUAL / INSTRUKCJA OBSŁUGI LED MOVING HEAD STRONG 108x3W RGBW WASH III F7000579c Table of contents 1 Introduction... 2 2 Safety information...
1 / 14 Content list / Spis Treści 1. Hardware and software requirements, preparing device to upgrade Wymagania sprzętowe i programowe, przygotowanie urządzenia do aktualizacji 2. Installing drivers and
I.1. X Have a nice day! Y a) Good idea b) See you soon c) The same to you I.2. X: This is my new computer. Y: Wow! Can I have a look at the Internet? X: a) Thank you b) Go ahead c) Let me try I.3. X: What
C IF16T CZUJKA KURTYNOWA PIR CURTAIN LENS INTRUSION DETECTOR INSTALACJA INSTALLATION 1. INTRODUCTION IF16Tis a curtain pir sensor, can create a barrier of protection useful for doors and windows. And it
APARATY GRZEWCZO WENTYLACYJNE ŚCIENNE WALL-MOUNTED HEATING AND VENTILATION UNIT Aparaty grzewczo-wentylacyjne typu AS są to urządzenia służące do przygotowania żądanej ilości powietrza o odpowiednich parametrach
TECHNICAL CATALOGUE WHITEHEART MALLEABLE CAST IRON FITTINGS EE Poland GENERAL INFORMATION USE Whiteheart malleable cast iron fittings brand EE are used in threaded pipe joints, particularly in water, gas,
SNMP Protocol The Simple Network Management Protocol (SNMP) is an application layer protocol that facilitates the exchange of management information between network devices. It is part of the Transmission
SIŁOWNIKI HYDRAULICZNE HYDRAULIC CYLINDERS Podwójnego działania Double acting SERIA VPM, VPM Series Uszczelnienie ISO, Seals ISO Ciśnienie robocze, Working pressure : 160 bar Średnice, Diameters : de 25
Has the heat wave frequency or intensity changed in Poland since 1950? Joanna Wibig Department of Meteorology and Climatology, University of Lodz, Poland OUTLINE: Motivation Data Heat wave frequency measures
TACHOGRAPH SIMULATOR DTCOSIM Service Manual USB-KSIM interface General description The simulator is a device that is used as a replacement for tachograph in the vehicle where the tachograph is not mandatory,
AGREGATY W WERSJI CHŁODZĄCEJ I POMPY CIEPŁA PICO-AE Pompy ciepła typu powietrze-woda - wentylatory osiowe - sprężarki typu Scroll Urządzenia te różnią się od Pico-A i Pico-C, ponieważ zostały specjalnie
Part-financed by EU South Baltic Programme w w w. p t m e w. p l PROSPECTS OF THE OFFSHORE WIND ENERGY DEVELOPMENT IN POLAND - OFFSHORE WIND INDUSTRY IN THE COASTAL CITIES AND PORT AREAS PORTS AS LOGISTICS
FLM-600 FOG MACHINES User manual FLM-600 Maszyna do dymu Instrukcja obsługi The guarantee for appropriate operation of the smoke machines is the using of the Flash-Butrym smoke liquid. www.flash-butrym.pl
Owner s manual English English Owner s manual Owner s manual English English Owner s manual Owner s manual English English Owner s manual Owner s manual English English Owner s manual Owner s manual English
Angielski bezpłatne ćwiczenia - gramatyka i słownictwo. Ćwiczenie 8 Przetłumacz na język angielski.klucz znajdziesz w drugiej części ćwiczenia. 1. to take a rest - odpocząć Muszę odpocząć. (5) Czy chcesz
Zawór hamowania przyczepy 45 10 Trailer control valve Przeznaczenie: Zawór steruj¹cy przyczepy stosowany jest w jednoprzewodowych i kombinowanych powietrznych uk³adach hamulcowych pojazdów samochodowych
WENYATORY PROMIENIOWE ROOF-MOUNTED CENTRIFUGA DACHOWE WPD FAN WPD Wentylatory promieniowe dachowe typu WPD przeznaczone są do Roof-mounted centrifugal fans type WPD are intended wentylacji wyciągowej pomieszczeń
Benefits Depending on your residency status (EU citizen or not) there are various benefits available to help you with costs of living. A8 nationals need to have been working for a year and be registered
Instrukcja obsługi cyfrowego tygodniowego wyłącznika czasowego Operating Instructions for Digital Weekly Timer 406-073 SV NO PL EN Bruksanvisning i original Bruksanvisning i original Instrukcja obsługi
Gotronik PPHU Dane aktualne na dzień: 19-01-2017 09:19 Link do produktu: /modul-odtwarzacza-plikow-mp3-audio-p-2905.html Moduł odtwarzacza plików MP3 audio Cena Dostępność Numer katalogowy 35,00 zł Dostępny
BULLETIN 2 II TRAINING CAMP POLISH OPEN MTBO CHAMPIONSHIPS 19-22.06.2014 MICHAŁOWO 23-29.06.2014 TRAINING CAMP WORLD MTB ORIENTEERING CHAMPIONSHIPS MASTERS WORLD MTB ORIENTEERING CHAMPIONSHIPS MTB ORIENTEERING
LCD (Liquid Crystal Display) Polarizing filter. Thin film with a vertical ais. Liquid crystal Polarizing filter. Thin film with a horizontal ais. Polarizing filter. Thin film with a horizontal ais. Polarizing
Configuring and Testing Your Network Network Fundamentals Chapter 11 Version 4.0 1 Konfigurowanie i testowanie Twojej sieci Podstawy sieci Rozdział 11 Version 4.0 2 Objectives Define the role of the Internetwork
WENTYLATORY PROMIENIOWE MEDIUM-PRESSURE CENTRIFUGAL ŚREDNIOPRĘŻNE TYPU WSP FAN TYPE WSP Wentylatory promieniowe średnioprężne typu WSP są wysokosprawnymi wentylatorami ogólnego i specjalnego przeznaczenia.
System aluminiowych szynoprzewodów oraz akcesoriów łączących, zasilających i montażowych. Do systemu można podpiąć wszystkie oprawy (reflektory) z oznaczeniem Adaptor 3F. Szyna wyposażona jest w dwa dodatkowe
e Hercules www.essystemk.com Strona 1/8 Page 1/8 e SPIS TREŚCI: 1. Informacje ogólne...3 General information 2. Informacje elektryczne...4 Electrical information 3. Informacje chłodnicze...5 Cooling information
VW MOTOMETER BOSCH METHOD 1 - OBD 2 METHOD 2 -DIAGNOSTIC OUTSIDE AFTER OPERATION YOU MUST DISCONECT ACU OR REMOVE FUSE FOR RESTART ODOMETER PO ZROBIENIU LICZNIKA ZDJĄĆ KLEMĘ LUB WYJĄĆ 2 BEZPIECZNIKI OD
The Overview of Civilian Applications of Airborne SAR Systems Maciej Smolarczyk, Piotr Samczyński Andrzej Gadoś, Maj Mordzonek Research and Development Department of PIT S.A. PART I WHAT DOES SAR MEAN?